one line incinerator for the destruction of hazardous medical waste.
Incinerator capacity of destruction of 350 kg/hour, calorific value of waste will be 13-25 MJ/kg
[3,500 kcal/kg] and maximum heat capacity 1,225,000 kcal/hr.
Incinerator destruction capacity will be 8.4 tons/day and operation time will be 24 hr./day.
Waste will be through automatic feeding system into the incinerator.
-The temperature will modulated in varying flow and percentage in oxygen, combustion gas is re-burned
in the re-combustion[secondary] chamber at a temperature of minimum 1,100 C during 2 seconds.
Control panel will be fitted with a functional synoptic view showing the operating situation of the whole
incinerator and controlled by DCS/PLC system.
Gas treatment system will respect the EE standard [Directive 2000/76/EC-4/12/2000.
TOC of slag and bottom ashes will be less 3% of the dry weight.
Installation will be completely free from visible smoke.
Incinerator will be designed as a Packaged unit, having electrical connection pre-wired and final pipes
Incinerator will have automatic de-ashing system with upward direction.
Incinerator will have flue gas treatment system inclusive [emergency by-pass stack, gas cooling system,
two reactors and particulates filtering system] and guarantee of emissions out of incinerator.
Training of AKU staffs at site.
Site may be inspected and examine existing ATI machine, capacity 150 kg/hr.in 24 hour operation.
Existing infrastructure space is available in basement, 100’ Length x 30’ wide x 20’ Height for 2nd Incinerator.
Existing chimney length is 12 meter, and width is 24”dia.
We plan to build a incinerator plant with 3 units of incinerators at the capacity of 500kg per hour each.
Together with other facilities like operation office, store, space to clean waste containers and 3-4 worker living quarters.
It is very much appreciated that if you can provide us a draft M/E drawing plan for the above facilities with 3 units of 500kg/h incinerator setup.
The incinerator must comply with ” Technical Standard NTON 05-015-02 Management and Solid Waste Disposal Hazardous co go ” , in addition to meeting international standards functionality standards for new stationary sources and emissions from the Environmental Protection Agency United States ( Environmental Protection Agency EPA ) Incinerators Medical and Hospital infectious waste ( HMIWI its acronym in English ) and the standards of the World Health Organization (WHO ) .
According to point 220.127.116.11 of the NTON 05-015-02 incinerator must have the following:
” Incinerators equipped with a camera primary and a secondary combustion , equipped with burners capable of achieving complete combustion of waste and widespread destruction of harmful and toxic chemicals (dioxins and furans among others) , attached to the solid waste bioinfectious .
a) primary combustion chamber , it requires a temperature of 800 ° C and one hour dwell to be destroyed waste produced ash and gas , including dioxins can generate cancer is found .
b ) In the secondary combustion chamber must reach temperatures around 1,100o C and must be operated with a residence time of the flue gases of a minimum of two seconds. To treat gas flow and entrained particles , before being released into the atmosphere , should be added towers chemical washing , cyclones , filters . “
The incinerator installed must comply with the design to ensure the destruction of all hazardous , biological , industrial waste and others. Combustion ” PYROLYTIC ” allows control of the gasification of waste and avoid significant release of black smoke and fine powder during loading . It also allows , regular and complete combustion of the waste.